Engine Generator 300kw Generator Set Made in China
|FOB Price:||US $3,860-98,620 / unit|
|Min. Order:||1 unit|
|Min. Order||FOB Price|
|1 unit||US $3,860-98,620/ unit|
|Transport Package:||Standard Export Wooden Box Packing|
|Payment Terms:||L/C, T/T, D/P, Western Union, Paypal, Money Gram|
- Model NO.: LHDG-500GF
- Installation Method: Fixed
- Cooling Method: Water Cooling
- Speed: Speed
- Usage: Common Units
- Excitation Mode: AC Rotating Exciter
- Exciting Method: Brushless
- Rated Frequency: 50 Hz
- Certification: Ce&ISO
- Engine Type: Z12V190bc--1
- Weight: 12500kg
- Specification: 6200x2100x2800mm
- HS Code: 8502200000
- Type: Self-Starting Diesel Generator
- Stroke: Four Stroke
- Output Type: AC Three Phase
- Conditions of Use: Land Use
- Landuse Type of Unit: Ordinary
- Diesel Engine: Cummins
- Color: Customized
- Rated Voltage: 230/400V
- Warranty: 1 Year or 1000 Running Hours Which Arrives First
- Rated Speed: 1500r/Min
- Trademark: Shandong Lvhuan
- Origin: Shandong, China
------------------------ Company Profile
Δ Established in 2008
Δ Factory area over 40000 square meters
Δ Over 260 employees, technicians over 100 people
Δ Provide repaire service free during the guarantee period
Δ Got the CE, ISO14001, ISO9001 certification
Δ Established cooperation relationship with Cummins
Δ Website www.Lvhuandongli.Com
|Engine Power||Cylinder Number||Cylinder Bore||Stroke||Displacement|
|Compression Ratio||Oil Capacity|
Δ Strong structure & Strengthen accessories
Δ Easy Start & ATS system
Δ Auto voltage regulation & Stable working condition
Δ Imported and easy-operation control system
Δ Imported and accurate gas control system
Δ Standard parts for easy maintain
Δ long life operation and low-operation cost
------------ Our Perfect Service
a) We will send our engineer to prospect the site of power station free of charge.
b) According to the situation of site, we will provide design drawings, such as power plant floor drawing, cooling system drawing, genset foundation, control room design, etc.
2. Sale service:
a) Operator training would be conducted by Lvhuan technicians during the process of commissioning or Factory training course in China,
b) Installation and commission of the genset would be instructed assisted by Lvhuan technicians at site.
3. After-sale service:
a) We have strong after-sale team, we will response within 24 hours and provide technical supports by phone or site guiding, help our clients to gain the biggeset profit.
b) For the quality problem, we will service for you free of charge during the guarantee period.
c) We provide one year guarantee period and lifetime service.
√ HOW TO CHOOSE THE RIGHT MODEL?
1. It depends on prime power, voltage,frequency and fuel type.
PLEASE TELL ME WHAT FUEL (NATURAL GAS, BIOGAS, BIOMASS GAS, WOOD SYNGAS, METHANE, COAL GAS) OR RAW MATERIAL (LIKE WOOD, GRASS, NUTSHELL ETC).
2. Our salesman and engineers are always available at your service.
√ WHAT IS THE OIL CONSUMPTION AND CAPACITY PER HOUR?
1. 1.0---1.63 g of lubricant oil consmption per hour.
1.0 cubic meter gas can produce 1.5-3.0 kw/h power.
√ WHAT THE OVERHAUL?
About 30,000 working hours. One week is enough to finish. We offer manual for weekly, monthly and overhaul maintenance.
√ WHAT IS THE WARRANTY?
One year. We offer all spare parts FREE of charge during warranty period. After this period, spare parts are not free. What's more, a set of spare parts will be shipped together with generator set free of charge.
√ HOW TO MAKE AN ORDER?
Just send inquiry / message to our sales. And we will reply and offer the details as soon as possible according to your request.
With professional and honest, we have established many business relationships with companies in Congo, Italy, Turkey, Vietnam, Thailand, Japan...Here are some pictures.
Notice About Power Plant Construction ! ! ! ! ! ! ! ! ! ! ! ! !
× Generator Room is usually constructed in open or semi-open type. The floor should be easily to clean and not easily to spark.
× If you want to construct Closed Generator Room, you must construct a single storey building. The open direction of all the doors and windows must turn outside. Please install some big capacity displacement device to avoid gas gathering.
× Generator Room and the Operation Room must be separated, can not be directly connected. The observation window should be with double deck glass protected by steel wire mesh.
× Lightning arrester is necessary.
× Prepar enough fire extinguishing appliances.
× "NO FIRE" mark should be obvious, open flame in the generator room is not allowed.
× In the exhaust gas, there are combustible gas. So, the exhaust pipe of the generator must be leaded to outside of room. The exhaust pipe must be connected tightly.