Cheap China Electric Biomass Generator Set for Africa
|FOB Price:||US $8,900-109,800 / unit|
|Min. Order:||1 unit|
|Min. Order||FOB Price|
|1 unit||US $8,900-109,800/ unit|
|Payment Terms:||L/C, T/T, D/P, Western Union, Paypal, Money Gram|
- Model NO.: LHBMG600
- Certification: CCC, ISO, TLC, CE
- Standard: Standard
- Speed: 1000rpm
- Rated Power: 250kw
- Power Factor: 0.8
- OEM: Yes
- Control System: Automatic Alarm System
- Transport Package: Standard Export Wooden Box Packing
- Origin: Shandong, China
- Power: 20kw-600kw
- Output Type: AC Three Phase
- Name: Factory Price Biomass Generator Set
- Frequency: 50/60Hz
- Output Voltage: 400V/230V
- Service: One Year
- Weight: 8200kg
- Trademark: Shandong Lvhuan
- Specification: 5300x1970x2170mm
- HS Code: 8502200000
|Model Number (Engine Type)||LHNG250|
|Prime Power/Standby Power||240KW/300KW|
|Phase||AC 3-Phase, 4 wire|
|Voltage Stable time||≤1s|
|Engine Capacity||32 L|
|Starting System||DC 24V electric motor|
|Cooling method||Water cooler|
|Lubricant method||Passive and flying lubricant|
|Power Factor||0.8 lagging|
|Colour||According to your request|
|Certificates||ISO 9001:2008, CE|
|Warranty||1 year or 1000 running hours arrives first|
|Control system||Automatic alarm system|
-----------------------------------Requirements For Biomass Gas Genset Working Condition
Within 1m from pressure regulating valve of gas intake
Gas temperature ≤ 40ºC
Pressure 3-20kpa, pressure changing rate ≤ 1kpa/min
H2S ≤ 200mg/Nm3
NH3 ≤ 20mg/Nm3
Tar Contecnt ≤ 20 mg/Nm3
Heat value ≥ 4.2MJ/Nm3
Impurity particle size ≤ 5μm, impurity content ≤ 30mg/Nm3
Moisture content ≤ 40g/Nm3
------------------------ Company Profile
Δ Established in 2008
Δ Factory area over 40000 square meters
Δ Over 260 employees, technicians over 100 people
Δ Provide repaire service free during the guarantee period
Δ Got the CE, ISO14001, ISO9001 certification
Δ Established cooperation relationship with Cummins
Δ Website www.Lvhuandongli.Com
We have established so many business relationship with many friends around the world.
Δ Strong structure & Strengthen accessories
Δ Easy Start & ATS system
Δ Auto voltage regulation & Stable working condition
Δ Imported and easy-operation control system
Δ Imported and accurate gas control system
Δ Standard parts for easy maintain
Δ long life operation and low-operation cost
√ HOW TO CHOOSE THE RIGHT MODEL?
1. It depends on prime power, voltage,frequency and fuel type.
PLEASE TELL ME WHAT FUEL (NATURAL GAS, BIOGAS, BIOMASS GAS, WOOD SYNGAS, METHANE, COAL GAS) OR RAW MATERIAL (LIKE WOOD, GRASS, NUTSHELL ETC).
2. Our salesman and engineers are always available at your service.
√ WHAT IS THE OIL CONSUMPTION AND CAPACITY PER HOUR?
1. 1.0---1.63 g of lubricant oil consmption per hour.
1.0 cubic meter gas can produce 1.5-3.0 kw/h power.
√ WHAT THE OVERHAUL?
About 30,000 working hours. One week is enough to finish. We offer manual for weekly, monthly and overhaul maintenance.
√ WHAT IS THE WARRANTY?
One year. We offer all spare parts FREE of charge during warranty period. After this period, spare parts are not free. What's more, a set of spare parts will be shipped together with generator set free of charge.
√ HOW TO MAKE AN ORDER?
Just send inquiry / message to our sales. And we will reply and offer the details as soon as possible according to your request.
Notice About Power Plant Construction ! ! ! ! ! ! ! ! ! ! ! ! !
× Generator Room is usually constructed in open or semi-open type. The floor should be easily to clean and not easily to spark.
× If you want to construct Closed Generator Room, you must construct a single storey building. The open direction of all the doors and windows must turn outside. Please install some big capacity displacement device to avoid gas gathering.
× Generator Room and the Operation Room must be separated, can not be directly connected. The observation window should be with double deck glass protected by steel wire mesh.
× Lightning arrester is necessary.
× Prepar enough fire extinguishing appliances.
× "NO FIRE" mark should be obvious, open flame in the generator room is not allowed.
× In the exhaust gas, there are combustible gas. So, the exhaust pipe of the generator must be leaded to outside of room. The exhaust pipe must be connected tightly.
Welcome to inquiry !